2006 Volume 126 Issue 10 Pages 1013-1022
Since a distribution network has many sectionalizing switches, there are huge radial network configuration candidates by states (opened or closed) of sectionalizing switches. Recently, the total number of distributed generation such as photovoltaic generation system and wind turbine generation system connected to the distribution network is drastically increased. The distribution network with the distributed generators must be operated keeping reliability of power supply and power quality. Therefore, the many configurations of the distribution network with the distributed generators must be evaluated multiply from various viewpoints such as distribution loss, total harmonic distortion, voltage imbalance and so on. In this paper, the authors propose a multi evaluation method to evaluate the distribution network configuration candidates satisfied with constraints of voltage and line current limit from three viewpoints ((1) distribution loss, (2) total harmonic distortion and (3) voltage imbalance). After establishing a standard analytical model of three sectionalized and three connected distribution network configuration with distributed generators based on the practical data, the multi evaluation for the established model is carried out by using the proposed method based on EMTP (Electro-Magnetic Transients Programs).